Insights: Four Steps to Controlling Legionella Growth in Cooling Towers
Taking these measures can prevent disease outbreaks such as Legionnaires’.
By Richard Gerbe, Co-Founder of HIGHMARK
No building should be making people sick; however, because of poor maintenance and cleaning efforts, the water in cooling towers has the ability to serve as the breeding ground for a variety of bacteria. One such bacterium is Legionella, the root cause of the recent major Legionnaires’ disease outbreak in New York City that sadly claimed several lives and sickened many people.
However, this situation is completely avoidable since technologies exist today to ensure cooling towers are kept clean. The dust and debris that bacteria like to propagate in can be removed and kept out through proper maintenance, filtration, water treatment, and monitoring. This will control the growth of bacteria, such as Legionella, and ensure that outbreaks, such as Legionnaires’, are prevented.
COOLING TOWERS AND LEGIONELLA
Cooling towers are an energy-, space- and cost-effective way to remove heat generated by centralized air conditioning systems from large buildings. The towers do this by using water and an evaporation process to pull the heat away and transfer it outside, thus creating a comfortable indoor environment.
An unwanted byproduct of this process is the collection of dust and debris that settles in the basin of the cooling tower. The problem is that if the cooling tower is left unmaintained, then bacteria will flourish in this particle concoction due to the presence of ideal growing conditions, which for Legionella include:
- Warm water stagnation;
- Water temperatures from 68° to 122°F with an optimal growth range of 95° to 115°;
- pH levels between 5.0 and 8.5;
- Sediment that tends to promote the growth of commensal microflora; and
- The presence of microorganisms, including algae, flavobacteria, and Pseudomonas, which supply essential nutrients and protection.
(Note: Ideal Legionella growing conditions provided by the Occupational Safety and Health Administration (OSHA): https://www.osha.gov/dts/osta/otm/otm_iii/otm_iii_7.html.)
CONTROLLING LEGIONELLA GROWTH IN COOLING TOWERS
If the proper steps for taking care of a cooling tower aren’t followed, then Legionella growth is encouraged. In order to control Legionella bacterial growth and consequently prevent disease outbreaks, there are four key steps to take for establishing a clean cooling tower that performs to expectations. These steps consist of: regular maintenance, systematic filtration, water treatment, and continuous monitoring.
1. Regular Maintenance
Cooling towers continuously wash the air as they operate, and because of this they are constantly collecting debris. The first step in removing what has settled in the tower and thus keeping it as clean as possible is regular maintenance. This includes:
- Conducting ongoing inspections to identify any mechanical deficiencies;
- Repairing any mechanical issues a cooling tower may have — such as leaks and broken panels, fans, and infill — so it operates as designed;
- Ensuring drift eliminators are sufficient and functional; and
- Performing regular cooling tower cleanings.
2. Systematic Filtration
Even if regular maintenance of the cooling tower is happening, dust and debris will still enter and collect in the basin of the tower. Therefore, the cooling tower water must be filtered on a continuous basis to remove the debris at, or close to, the hypothetical rate of collection to impede build-up or accumulation. The specific goals of filtration include:
- Removing dust and debris that are pulled into the cooling tower;
- Capturing organic compounds and biological organisms; and
- Eliminating food and hiding places that foster bacterial development.
3. Water Treatment
Water treatment is also an essential component, and depends on the application and type of system, as well as the location. The process is specific to each building and the benefits include:
- Controlling scale formation;
- Governing pH levels of the system water;
- Reducing corrosion and fouling; and
- Avoiding biological contamination.
4. Continuous Monitoring
Finally, continuous automatic system monitoring and commissioning are necessary for both enhancing water quality and system performance. This process consists of:
- Deploying equipment and software dedicated solely to monitoring cooling-system water;
- Monitoring water quality and system efficiency;
- Alerting building personnel to a potential decline in water quality; and
- Providing historical records of water quality.
INNOVATIVE TECHNOLOGIES AVAILABLE TODAY
There are many innovative technologies on the market today that can help control the growth of Legionella in cooling towers. Two of the most effective include:
Symphony is a constant-commissioning analytics solution that examines building water quality in near real-time and alerts operators to any issues. It’s impossible to manage what you don’t measure, and Symphony will give an early indication of biofilm activity, which is usually a precursor to Legionella development. This helps to control bacterial growth and to maintain an efficient and reliable cooling system.
VAF Filtration Systems™
VAF solutions consist of state-of-the-art, self-cleaning screen filtration technology that can be applied to cooling towers. With basin water kept in perpetual motion, a VAF filter is able to screen out tiny particles of dust and debris, including sand, silt, scale particles, rust particles, algae, and chemical residue. This precise filtration discourages the growth of Legionella.
The Legionnaires’ outbreak is a tragic and avoidable occurrence. Cooling towers should never be at the center of any disease epidemics since technologies exist today to ensure maximum cleanliness and operational efficiency. By following the process of proper maintenance, filtration, treatment, and monitoring, the growth of Legionella in cooling towers can be controlled and the health of the public can be protected.
To view the full article in ENR New York, click here.
To view the full article in ACHR News, click here.
World Environment Day 2020: A Time For Nature and Building EfficiencyA Time for Nature and Biodiversity World Environment Day is a global day of environmental action, with a 2020 focus on a "time for nature" and a theme of "biodiversity." Such critical messages are...
On-Demand Webinar Prevent the Spread of Infections with PCO Air PurifiersWebinar Overview Topic: HVAC filters miss smaller indoor air contaminants, such as viruses, bacteria and VOCs. The solution is Genesis Air Photocatalytic Oxidation (PCO) Air Purifiers, which...
Earth Day 2020: Why Building Efficiency is Critical Post-COVID-19A COVID-19 Positive? The Environment Out of all the destruction and chaos caused by the Coronavirus (COVID-19), there’s been one tremendously positive effect. The environment has benefitted greatly with...